Conductor: 2 AWG through 750 kcmil bare copper compact, Class B strand.
Extruded Strand Shield (ESS): Thermoset semi-conducting stress-control layer over conductor.
Insulation: Ethylene Propylene Rubber (EPR) insulation, colored to contrast with black conducting layers.
Extruded Insulation Shield (EIS): Thermoset semi-conducting polymeric layer, free stripping from insulation.
Shield: 5 mil annealed copper tape with a minimum 25% overlap.
Ground: Annealed bare copper Class B stranding per ASTM B8.
Armor: Aluminum Interlocked Armor (AIA)
Jacket: Flame-retardant moisture- and sunlight-resistant Polyvinyl Chloride (PVC), red.
For use in wet or dry locations, indoors or outdoors, in exposed or concealed work. May be used in cable trays or on approved support in protected areas. Permitted for use in Class I; Class II, Division 2; and Class III, Divisions 1 and 2 hazardous locations per the NEC. Ideal for use in commercial, industrial and utility applications where space is limited and reliability, maximum performance, ease of installation and fire resistance are important.
Rated at 105oC wet or dry. Excellent heat and moisture resistance. Outstanding corona resistance. Flexible for easy handling. High dielectric strength. Low moisture absorption. Electrically stable under stress. Low dielectric loss. Chemical- and radiation-resistant.
Excellent crush resistance. Cost-effective alternative to installations in conduit. Meets cold bend test at -25oC.
Industry: UL 1072. ICEA S-93-639/NEMA WC74. AEIC CS8. UL Type MV-105. UL Type MC.
Flame Test: IEEE 383 (70,000 BTU/hr). UL 1581 (70,000 BTU/hr). IEEE 1202 (70,000 BTU/hr) CSA FT4. ICEA T-29-520 (210,000 BTU/hr).
ICEA T-30-520 (210,000 BTU/hr).
Other: EPA 40 CFR, Part 261, for leachable lead content per TCLP. OSHA acceptable.
*AMPACITY for cables installed in uncovered cable tray without maintained spacing: 105℃ conductor temperature, 40℃ ambient.
**AMPACITY for cables installed in uncovered cable tray with maintained spacing of one cable diameter: 105℃ conductor temperature, 40℃ ambient.
For other installation conditions refer to the NEC