Conductor: Aluminum or Copper
Standard: IEC 60502, BS 7870, GB/T12706 Etc.
Packaging: Iron Or Wooden Drum
Conductor: Cu or Aluminum, Insulation:PVC Sheath: PVC
Sheath Color: Black or Colors
PVC insulated PVC sheathed power cable (PVC/PVC Cable)
Flame retardant PVC insulated PVC sheathed power cable (FR/PVC/PVC Cable)
1. PVC power(fire resistant) cables suitable for electrical power transmission and distribution lines with AC rated voltage U0/U up to and including 0.6/1 kV.
Note: the single core armored cables are used for D.C. system only. As for A.C. system, armor layer should be used of non-magnetic material or magnetic isolation measures.
2.It to be used for outdoor and indoor installation in damp and wet locations, in tunnel, in down wells,cable furrow or pipe,underground.
BS 7870-3.10-2001 orIEC 60502, BS, DIN, or others as per customer’s country
1.The long time working temperature is at 90℃, suffer short circuit (within 5
seconds), the temperature of core can not higher than 250℃
2.The ambient temperature should not lower than -10℃
3.The laying temperature should not lower than 0℃
4.Single core’s bend radius with no armor should not exceed 20D,single core’s bend
radius with armor should not exceed than 15D,three cores’ bend radius with armor
should not exceed 12D.
|Cu Conductor||Al Conductor|
|VV||VLV||Copper/Aluminium core,PVC insulated,PVC sheathed power cable||Non-armoured PVC cable are suited for laying indoors,In cable trench,On cable racks and in pipes. Unable bear external pressures and tensions|
|VV||VLV||Copper/Aluminium core,PVC insulated,PE sheathed power cable|
|Type||No. of Core||Nominal cross-section of conductor mm2|
|Cu(AL)/PVC/PVC||1,2,3,4,5 ， 3+1,4+1,3+2||1.5-1000|
|Number of Cores & Nominal Cross-section Area|
|Number of Cores||1||2||3||3+1||4||4+1|
|Section Area (mm 2 )||1.5 - 500||1.5 - 500||2.5 - 300||4 - 300||2.5 - 300||2.5-300|